not only is it installed incorrectly. you can not use that valve on a sprinkler system under upc code see upc 603.2.2/ table 6-2 note 4 not to be subject to operating pressure for more than 12 hours in a 24 hour period the valve that needs to be used is a double check backflow preventer. $$$ i would call his office and tell them they have installed a valve that is not code compliant tell them to install the correct valve.. AT NO ADDITIONAL cost to you. and when they are thru. you will be expecting the test certification report from a 3rd party. at THAT time, you will call the state inspector to have a look see if they give you a hard time. CALL the plumbing inspector for a sprinkler system backflow inspection the inspector will go ballistic...
Thanks Frodo. Much appreciated. As it is today, does that valve actually do anything (even though it is the wrong one)?
it is doing nothing.
Bathroom remodeling can be a fun DIY project to build your dream bathroom, your oasis of escape fro
Tired of your old pipeline that you keep on repairing every now and then? Tired of companies that c
Inspecting the quality of your plumbing is essential to your home?s health. It?s wise to have a pl
4 Tips afor National Resume Month Looking for a job can be stressful. Trying to put together a resu
Converting From Oil to Gas If you?re looking to replace your old, out-of-date oil heating equipment
Sump pumps are designed to fix the problem of flooding in the basement, but they can create problem
PFP Series 2.5 in. Stainless Steel Liquid Filled Case Pressure Gauge with 1/4 in. NPT CBM and Range of 0-100 psiBrand :- Winters Instruments Price :- $65.02
Twist Collection Single Hole 1-Handle Bathroom Faucet in Brushed NickelBrand :- Ultra Faucets Price :- $146.42
Crestfield 60 in. x 58-1/8 in. Semi-Frameless Sliding Bathtub Door in Bronze with Transition GlassBrand :- Delta Price :- $342.00
Indulgence 7.5kW Steam Bath Generator Package in Brushed NickelBrand :- SteamSpa Price :- $1,876.76