not only is it installed incorrectly. you can not use that valve on a sprinkler system under upc code see upc 603.2.2/ table 6-2 note 4 not to be subject to operating pressure for more than 12 hours in a 24 hour period the valve that needs to be used is a double check backflow preventer. $$$ i would call his office and tell them they have installed a valve that is not code compliant tell them to install the correct valve.. AT NO ADDITIONAL cost to you. and when they are thru. you will be expecting the test certification report from a 3rd party. at THAT time, you will call the state inspector to have a look see if they give you a hard time. CALL the plumbing inspector for a sprinkler system backflow inspection the inspector will go ballistic...
Thanks Frodo. Much appreciated. As it is today, does that valve actually do anything (even though it is the wrong one)?
it is doing nothing.
Being a real estate agent can be a tough job. There?s a lot of regulations to follow, it can take w
There?s something special about the New Year. The last weeks of December are often sort of quiet an
Many of us assume that our general plumbing systems will remain in great working order, throughout
a Plumbing emergencies are never fun. Unfortunately, they often strike without any warning, leaving
Commercial Plumbing Contractors In Houston Handle Some Typical Plumber Problems Just On A Bigger S
Here are some of the latest reviews from our customers this week: Brett arrived at the designated t
47 in. x 35.4 in. x 89 in. Steam Shower Enclosure Kit in BlackBrand :- Ariel Price :- $3,195.00
Sena Shower Arm in StarLight Chrome for Sena HandshowersBrand :- GROHE Price :- $18.00
34 in. x 60 in. Double Threshold Shower Base with Right Drain and Brushed Nickel Trench GrateBrand :- Redi Trench Price :- $761.00
36 in. x 48 in. x 88 in. 14-piece Retro Fit Over Existing Shower Surround in Worthington White/Silver StormBrand :- ForzaQuartz Seamless By Nature Price :- $1,800.00